Did you know that you can trigger complex sequences and scenes by pressing a wall-mounted push button with ayControl and EcoButler? And did you know that you can use IF/THEN logic in EcoButler rules?
- Implement large scenes, e.g. check-in/check-out functions, where users can themselves change the executed actions and delay times
- Scenes can control any device which is supported by ayControl, not only KNX; e.g. you also can control multimedia devices (via HTTP or Infrared), and even send push messages to mobile devices (“I’m at home”)
- You can trigger multiple rules with a single button. Rules can also be triggered my motion detectors.
- Even complex logic becomes possible: “Turn off the outdoor light when the weather station measures less than 20 Lux, and always turn off the music and set the heating to standby” .
- It is possible to integrate heating, alarm and security systems into rules.
Configuration of 1-bit KNX buttons triggering EcoButler rules
1. KNX, ETS
- Create a KNX group address. This address is used to trigger the EcoButler rule, but can optionally also control a KNX function.
- Assign this group address to the KNX button. The button has to be capable of sending the values 0 and 1 (1 bit) to the group address.
2. ayControl Editor
- Open your ayControl profile and import the KNX group address as a read address.
- Create a value display control based on that address which displays the value (0 or 1) of the address.
- Add the value display to all device layouts. We recommend to create a separate room for this kind of controls.
- Deploy the profile on the mobile device.
3. ayControl + EcoButler
- Open the ayControl app on your device. Connect to the EcoButler and create a new rule.
- Add the condition “Value display value” and select the previously created value display control. Set the condition to equal the value 1.
- You can add additional conditions. These conditions have to be met when the button is pressed in order to execute the rule actions.
- Now add the actions that should be executed when the button is pressed. You can delay the execution of control actions by inserting a Wait action before them.
- Save the rule. Now you should be able to execute your actions by pressing the wall-mounted button.
Expert Tip: Deactivate or reset the actions using the same KNX button
- Create another rule and add a condition for the same value display control as before, this time matching the value 0.
- For each action in the first rule, add an “inverted action” which resets or reverts the original action (e.g. when turning a light on in the first rule, turn the same light off in the second rule).
- Save the rule. Done!
More ideas for EcoButler rules
- Logic: do not lower the blinds when it is too windy outside.
- When you press the button for “going to sleep”, the EcoButler can send you an alert message to your mobile device if you left the garage door open.
The post Trigger EcoButler rules with wall-mounted push buttons appeared first on ayControl KNX.